1 Phase Surge Protection Device, 120/240VAC
- Item # 19L437
- My Part #
- Mfr. Model # STV100K10S
- Catalog Page # N/A
- UNSPSC # 39121610
Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
- Item Surge Protection Device
- Phase 1
- Voltage 120/240VAC
- Max. Continuing Operating Voltage 150/300VAC
- Voltage Protection Rating 600V (L-N), 700V (L-G, N-G), 1000V (L-L)
- Nominal Discharge Current 3kA
- Modes of Protection L-G, L-L, L-N, N-G
- Modular / Nonmodular Nonmodular
- Mounting Style 1/2" NPT Offset Nipple
- Enclosure Material Sand Encapsulation
- Enclosure NEMA Rating 12
- Length 4.00"
- Width 6.00"
- Depth 4.00"
- Max. Surge Current Per Phase 100kA
- Max. Surge Current Per Mode 50kA (L-N, L-G, N-G)
- Noise Attenuation 40dB
- Short Circuit Current Rating 65kAIC
- Number of Poles 2
- Number of Wires 3 Wires + Ground
- Wire Gauge 12 AWG
- Standards UL/cUL Listed
- Green Environmental Attribute Does not Contain Reproductive or Developmental Toxins (as Per State of CA List), Endocrine Disrupters (as Per European Union Priority For Research List), Asthmagens (as Per AOEC List), Carcinogens (as Per IARC 1-2A-2B Lists)
Compliance and Restrictions
- This item has been designated by the manufacturer as an environmentally preferable product (EPP) because this item is Does not Contain Reproductive or Developmental Toxins (as Per State of CA List), Endocrine Disrupters (as Per European Union Priority For Research List), Asthmagens (as Per AOEC List), Carcinogens (as Per IARC 1-2A-2B Lists).
Alternate Search Terms
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.