1-1/2" Aluminum Fuel Gas Solenoid Valve, Normally Closed
- Item # 38VC41
- My Part #
- Mfr. Model # 8215G070-12/DC
- Catalog Page # 2879
- UNSPSC # 40141605
Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
- Item Fuel Gas Solenoid Valve
- Solenoid Valve Product Group Fuel Gas Solenoid Valve
- Valve Ways and Positions 2-Way/2-Position
- Valve Configuration Normally Closed
- Media - Valves Fuel Gas
- Pipe Size - Valves 1-1/2"
- Min. Operating Pressure Differential 0 psi
- Max. Operating Pressure Differential Air/Inert Gas 25 psi
- Max. Operating Pressure Differential Water 25 psi
- Environmental Rating - Valves Indoor,Outdoor
- Voltage 12VDC
- Coefficient of Volume 35
- Body Material - Valves Aluminum
- Coil Insulation Class F
- Seal Material - Valves NBR
- Max. Operating Pressure Differential 25 psi
- Orifice Dia. 1-5/8"
- Ambient Temp. Range 32 Degrees to 77 Degrees F
- Watts 35.1
- NEMA Rating 1, 2, 3, 3S, 4, 4X
- Coil Enclosure General Purpose Junction Box and Watertight
- Electrical Connections 1/2" Conduit with 18" Leads
- Max. Fluid Temp. 104 Degrees F
- Hz 60
- Overall Length 5"
- Overall Width 5-13/32"
- Overall Height 6-45/64"
- Center Line Pipe Center Size 5-1/2"
- Application For On-Off Control of Fuel Gas in Commercial and Industrial Gas Burners
- Standards UL and CSA for Safety Shutoff
Compliance and Restrictions
Alternate Search Terms
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.