Commercial/Industrial 230/208VACV Portable Air Conditioner, 24,000 BtuH Cooling
- Item # 4YN29
- My Part #
- Mfr. Model # OFFICE PRO 24
- Catalog Page # 3058
- UNSPSC # 40101701
Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
- Item Portable Air Conditioner
- Environmental Applications - Air Conditioners and Heat Pumps Commercial/Industrial
- Voltage - Air Conditioners and Heat Pumps 230/208VAC
- BtuH Cooling 24,000
- Item - Air Conditioners and Heat Pumps Portable Air Conditioner
- NEMA Plug Configuration - Air Conditioners and Heat Pumps 6-20P
- Fan-Only Speeds 2
- Number of Cooling Speeds 2
- Cooling Method Air-Cooled
- Control Type Programmable
- Width 21"
- Depth 27"
- Height 49"
- Hz 60
- Phase 1
- Watts 2900
- Amps 13.2
- Max. Supply Hose Length 50 ft.
- Max. Exhaust Hose Length 45 ft.
- Sound Level dBA 63/61
- Exhaust CFM 870/760
- Supply CFM 630/545
- Ambient Operating Range 65 to 95 Degrees F
- Condensate Tank Capacity 5 gal.
- Power Cord Length 6 ft.
- Includes Compressor Short-Cycle Overload Protection, Two-Speed Fans, Adjustable Louvers, and Fan Motor Protection
- Standards cETLus
Compliance and Restrictions
Alternate Products may not be identical in style or function to original selection. Please compare below for more information.
Item # 5AE85MOVINCOOL
Product Reviews Disclaimer:
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.