1/50 HP 115V Evaporative Cooler Pump
- Item# 3CB60
- Mfr. Model# CP2-115
- Catalog Page# 3351
- UNSPSC# 40151510
Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
- Item Pump
- Type Evaporative Cooler
- HP 1/50
- Voltage 115
- Length (In.) 4-1/4
- Width (In.) 4-1/4
- Height (In.) 9
- Inlet/Outlet (In.) 5/8, 3/4
- RPM 3000
- Motor Type Shaded Pole
- Motor Enclosure OFC
- CFM 7500-15,000
- GPH of Water @ 1 Ft. of Head 502
- GPH of Water @ 2 Ft. of Head 467
- GPH of Water @ 3 Ft. of Head 440
- GPH of Water @ 5 Ft. of Head 371
- GPH of Water @ 8 Ft. of Head 294
- GPM of Water @ 1 Ft. of Head 8.3
- GPM of Water @ 3 Ft. of Head 7.3
- GPM of Water @ 5 Ft. of Head 6.1
- GPM of Water @ 9 Ft. of Head 2.91
- Shut-Off (Ft.) 11
- Max. Immersion Depth (In.) 4
- Body Material Polystyrene
- Max. Recommended Viscosity 50 SSU
- Max. Temp. 122
- Cord (Ft.) 4
- Application For Evaporative Coolers, Displays, Laboratories, Water Transfer Uses
- For Use With Nonflammable Liquids Compatible with Pump Materials
Compliance and Restrictions
This product contains a chemical that is regulated under California Proposition 65.
Warning: This product contains a chemical known to the State of California to cause cancer.
Warning: This product contains a chemical known to the State of California to cause birth defects or other reproductive harm.
Alternate Products may not be identical in style or function to original selection. Please compare below for more information.
Alternate Search Terms
Product Reviews Disclaimer:
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.