1/3 HP Sump/Battery Back-Up Combination System, Discharge NPT (In.): 1-1/2, Max. Flow (GPH): 2700
- Item# 10V134
- Mfr. Model# PC237-441
- Catalog Page# 3265
- UNSPSC# 40151512
Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
- Item Sump/Battery Back-Up Combination System
- HP 1/3
- Discharge NPT 1-1/2"
- Voltage 115
- Voltage - Back-Up 12VDC
- Amps 5.2
- Amps - Back-Up 13
- Switch Type Vertical Float
- 12VDC Battery Charger 900 mA
- Max. Flow (GPH) 2700
- Max. Flow (GPH) - Back-Up 2700
- Max. Head 21 ft.
- Max. Head (Ft.) - Back-Up 24
- Max. Dia. Solids 3/8"
- Max. Dia. Solids (In.) - Back-Up 1/4
- GPH of Water @ 0 Ft. of Head 2700 (Primary); 2040 (Secondary)
- GPH of Water @ 5 Ft. of Head 2280 (Primary); 1530 (Secondary)
- GPH of Water @ 10 Ft. of Head 1800 (Primary); 960 (Secondary)
- GPH of Water @ 15 Ft. of Head 1200 (Primary); 360 (Secondary)
- Max. Liquid Temp. 140 Degrees F
- Min. Sump Pit Dia. 15"
- On Point (In.) 7 (Primary); 11.5 (Secondary)
- Off Point (In.) 3 (Primary); 9.5 (Secondary)
- Base Material Polypropylene (Primary); Nylon (Secondary)
- Housing Material Aluminum (Primary); ABS Plastic (Secondary)
- Impeller Material Polypropylene (Primary); Nylon (Secondary)
- Motor Type PSC (Primary); Brush Type DC (Secondary)
- Duty Continuos (Primary); Intermitent (Secondary)
- Shaft Seal Buna N Double Lip (Primary); Buna N Double Lip (Secondary)
- Length 15-1/2"
- Width 10"
- Height 21-1/2"
- Cord Length 10 ft. (Primary); 8 ft. (Secondary)
- For Use With Sump Pits Above 15" Diameter and 18" Deep
- Agency Compliance CSAc,us (Primary)
- Includes Check Valves, Battery Box and Charger
- Off Point 3 (Primary); 9.5 (Secondary)
- On Point 7 (Primary); 11.5 (Secondary)
Compliance and Restrictions
This product contains a chemical that is regulated under California Proposition 65.
Warning: This product contains a chemical known to the State of California to cause cancer.
Warning: This product contains a chemical known to the State of California to cause birth defects or other reproductive harm.
Alternate Search Terms
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.