Ceiling Ventilator, 780 CFM, 115 V
- Item# 5AE77
- Mfr. Model# 5AE77
- Catalog Page# 3686
- UNSPSC# 40101502
Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
- Item Ceiling Ventilator
- Singlewide / Doublewide Singlewide
- Insulated Yes
- CFM @ 0.000-In. SP 812
- CFM @ 0.100-In. SP 782
- CFM @ 0.125-In. SP 775
- CFM @ 0.250-In. SP 741
- CFM @ 0.375-In. SP 704
- CFM @ 0.500-In. SP 665
- CFM @ 0.625-In. SP 625
- CFM @ 0.750-In. SP 581
- Sones @ 0.000-In. SP @ 5 Ft. 8.4
- Sones @ 0.100-In. SP @ 5 Ft. 8.3
- Sones @ 0.125-In. SP @ 5 Ft. 8.3
- Sones @ 0.250-In. SP @ 5 Ft. 7.9
- Voltage 115VAC
- Hz 60
- Phase 1
- Full Load Amps 3.30
- Number of Speeds 1
- Watts 348
- Motor RPM 1600
- Motor Type Permanent Split Capacitor
- Motor Enclosure Open Dripproof
- Motor Insulation Class B
- Max. Inlet Temp. 104 Degrees F
- Housing Height 14-1/2"
- Housing Width 14-3/8"
- Housing Length 18"
- Discharge Height 8"
- Discharge Width 10"
- Grille Length 19-3/8"
- Grille Width 16-3/8"
- Grille Material Aluminum
- Grille Color White
- Mounting Position Ceiling, Horizontal or Vertical
- Housing Material Galvanized Steel
- Wheel Material Polypropylene
- Speed Control 48C172
- Standards UL/cUL 507, AMCA Air and Sound
- For Use With General Ventilation Applications
- Includes Backdraft Damper, Hardware and Mounting Brackets
- Recommended Accessories 48C172
Compliance and Restrictions
Alternate Search Terms
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.