1/3HP 115V Double Inlet Forward Curve Blower with Motor
- Item# 1XJX9
- Mfr. Model# 1XJX9
- Catalog Page# 3720
- UNSPSC# 40101601
Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
- Item Blower with Motor
- Type Double Inlet Forward Curve
- Drive Type Direct
- Speed 4
- Wheel Dia. 9-7/16"
- Wheel Width (In.) 9-7/16
- CFM Range 1638 to 813 @ 0.300-In SP to 0.900-In SP
- CFM @ 0.000-In. SP # # # #
- CFM @ 0.300-In. SP 1638 1516 1368 1132
- CFM @ 0.400-In. SP 1610 1496 1310 1101
- CFM @ 0.500-In. SP 1545 1437 1280 1083
- CFM @ 0.600-In. SP 1457 1373 1256 1046
- CFM @ 0.700-In. SP 1358 1320 1185 1012
- CFM @ 0.800-In. SP 1225 1139 1052 896
- CFM @ 0.900-In. SP 1050 926 826 813
- CFM @ 1.000-In. SP - - - -
- CFM @ 1.10-In. SP - - - -
- CFM @ 1.200-In. SP - - - -
- CFM @ 1.250-In. SP - - - -
- CFM @ 1.30-In. SP - - - -
- CFM @ 1.40-In. SP - - - -
- CFM @ 1.500-In. SP - - - -
- CFM @ 1.600-In. SP - - - -
- CFM @ 1.70-In. SP - - - -
- CFM @ 1.80-In. SP - - - -
- Max. Inlet Temp. (Deg. F) 104
- Max. Ambient Temp. (F) 104
- Voltage 115
- Hz 60
- Phase Single
- Full Load Amps 6.9
- Motor HP 1/3
- Motor RPM 10851040937858
- Motor Type Permanent Split Capacitor
- Bearing Type Ball
- Motor Enclosure Open Dripproof
- Housing Height (In.) 15-9/32
- Housing Width (In.) 12-5/16
- Housing Depth (In.) 15
- Discharge Height (In.) 10-1/4
- Discharge Width (In.) 11-13/16
- Mounting Multipostion
- Housing Material Steel
- Housing Finish Gray
- Wheel Material Steel
- Speed Controllable No
- Assembled/Unassembled Assembled
- Agency Compliance CE
- Footnotes # Motor Overload Condition
Compliance and Restrictions
This product contains a chemical that is regulated under California Proposition 65.
Warning: This product contains a chemical known to the State of California to cause cancer.
Warning: This product contains a chemical known to the State of California to cause birth defects or other reproductive harm.
Alternate Search Terms
Product Reviews Disclaimer:
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.