3/4-HP Self Priming Centrifugal Pump, 52 ft. Max. Head, 3/8" Max. Dia. Solids, Cast Iron
- Item # 2ZXP2
- My Part #
- Mfr. Model # 2ZXP2
- Catalog Page # 2639
- UNSPSC # 40151503
Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
- Item - Self Priming Pumps Self Priming Centrifugal Pump
- HP - Pumps 3/4
- Voltage - Pumps 208 to 230/460VAC
- Phase - Pumps 3
- Max. Head - Pumps 52 ft.
- Best Efficiency Range GPM @ Head 14 to 52 gpm @ 45 to 20 ft.
- Housing Material - Pumps Cast Iron
- Motor Enclosure - Pumps Totally Enclosed Fan-Cooled
- Max. Dia. Solids - Pumps 3/8"
- Inlet Size - Pumps 1-1/2" NPT
- Outlet Size - Pumps 1-1/2" NPT
- Self-Priming Yes
- Amps 2.5-2.4/1.2
- Wetted Materials Cast Iron, Buna-N, Carbon, Ceramic, Stainless Steel
- Hz 60
- Max. Pressure - Pumps 22 psi
- Max. Temp - Pumps 200 Degrees F
- Port Rotation - Pumps No
- Suction Lift - Pumps 6 ft.
- Motor Design 3-Phase
- Seal Material Buna-N, Carbon, Ceramic, Stainless Steel
- Max. Specific Gravity 1.3
- Max. Case Pressure 75 psi
- Inlet Pressure 75 psi
- Impeller Type Semi Open
- Impeller Material Cast Iron
- Bearing Type Ball
- Duty - Pumps Continuous
- Agency Compliance c UL us
- Manufacturers Warranty Length 1 yr.
- Height 9-1/2"
- Length 16-5/32"
- Width 6-1/8"
- Includes Manual
- Frame 56J
- Motor RPM 3450
- GPM of Water @ 10 Ft. of Head 61
- GPM of Water @ 5 Ft. of Head 65
- GPM of Water @ 15 Ft. of Head 56
- GPM of Water @ 20 Ft. of Head 52
- GPM of Water @ 30 Ft. of Head 42
- GPM of Water @ 40 Ft. of Head 24
- GPM of Water @ 50 Ft. of Head 4
Compliance and Restrictions
Alternate Products may not be identical in style or function to original selection. Please compare below for more information.
Item # 2ZXP4DAYTON
Alternate Search Terms
Product Reviews Disclaimer:
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.