General Use Pleated Air Filter, 16x32x1, MERV 7, Standard Capacity, Synthetic, Beverage Board
- Item # 6FLZ9
- My Part #
- Mfr. Model # 6FLZ9
- Catalog Page # N/A
- UNSPSC # 40161505
Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
- Air Filter Item Pleated Air Filter
- Style - Air Filters Panel
- Performance Rating MERV 7
- Nominal Filter Size 16x32x1
- Filter Efficiency - Air Filters 35%
- Air Filter Capacity Standard Capacity
- Media Material Synthetic
- Frame or Header Material Beverage Board
- Common Applications General Use
- Media Color White
- Media Area 10.0 sq. ft.
- Pleats per Linear Foot 32
- Filters Out MERV 5-8 Mold, Spores, Dust Mites, Cat & Dog Dander, Hair Spray, Fabric Protector, Dusting Aids, Cement Dust, Pudding Mix
- Removes Particles Down To 3.0 to 10.0 microns
- Air Flow @ 300 fpm 1067 cfm
- Air Flow @ 500 fpm 1778 cfm
- Initial Resistance @ 300 fpm 0.22" WC
- Initial Resistance @ 500 fpm 0.37" WC
- Final Recommended Resistance 1.0" WC
- Max. Temp. 180 Degrees F
- Max. Velocity 500 fpm
- Filter Frame Color White
- Gasket Location None
- Gasket Material None
- Nominal Height 16"
- Nominal Width 32"
- Nominal Depth 1"
- Actual Filter Size 15-1/2"x31-1/2"x3/4"
- Actual Height 15-1/2"
- Actual Width 31-1/2"
- Actual Depth 3/4"
- Standards UL 900 Classified
- Item Pleated Air Filter
Compliance and Restrictions
Alternate Search Terms
Product Reviews Disclaimer:
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.