Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
1 HP Submersible Sump Pump, None Switch Type, Cast Iron Base Material
- Item # 4NW01
- Mfr. Model # N140
- UNSPSC # 40151512
- Catalog Page # 3673
- Shipping Weight 47.15 lbs.
- Item Submersible Sump Pump
- HP 1
- Switch Type None
- Cord Length 15 ft.
- Voltage 115
- Amps 12
- Dia. 10-1/8"
- Discharge NPT 1-1/2"
- Height 12-5/8"
- Max. Head 50 ft.
- Max. Dia. Solids 1/2"
- GPM of Water @ 5 Ft. of Head 86
- GPM of Water @ 10 Ft. of Head 80
- GPM of Water @ 15 Ft. of Head 73
- GPM of Water @ 20 Ft. of Head 66
- GPM of Water @ 25 Ft. of Head 59
- GPM of Water @ 30 Ft. of Head 50
- Max. Temp. 130 Degrees F
- Base Material Cast Iron
- Housing Cast Iron
- Top Material Cast Iron
- Impeller Material Polypropylene
- RPM 3450
- Thermal Protection Yes
- Shaft Seal Carbon/Ceramic
- Mechanical Seal CRB/CMC
Compliance and Restrictions
This product contains a chemical that is regulated under California Proposition 65.
Warning: This product contains a chemical known to the State of California to cause cancer.
Warning: This product contains a chemical known to the State of California to cause birth defects or other reproductive harm.
Item # 3BB72DAYTON
Price $365.00 / each
Alternate Search Terms
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.
Ask your questions. Share your answers.
To answer your question, this pump is designed to run "intermittently" that is "on" for aproximately 30 minutes off for around 10-15 then on again. But if this unit is fully submerged in water, it should be able to tollerate a few hours of continious run time. This unit will shut off if it becomes over heated, that will be a sign that it has run too long.. This is not a guarantee, you can check with Zoeller @ www.Zoeller.com.
I hope this answers your question, thanks for using Grainger Ask & Answer!
Grainger is neither responsible for, not does it endorse, the content of any statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger.