Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
- ItemSubmersible Sewage Pump
- Pump TypeAutomatic
- Switch TypeVertical Float
- Base MaterialPolypropylene
- HousingCast Iron
- Top MaterialCast Iron
- Impeller MaterialPolypropylene
- Shaft MaterialCarbon/Ceramic
- Cord Length15 ft.
- Discharge Size2"-NPT
- Max. Dia. Solids2"
- On Point12-1/2"
- Off Point4-1/2"
- GPM of Water @ 5 Ft. of Head90
- GPM of Water @ 10 Ft. of Head60
- GPM of Water @ 15 Ft. of Head22
- Max. Head18 ft.
- Max. Temp.130 Degrees F
- Thermal ProtectionYes
- Motor TypePermanent Split Capacitor, Hermetically-Sealed, Oil-Filled
- Bearing TypeSleeve
- Shaft SealCarbon/Ceramic
- StandardsUL Listed, CSA Certified
- Warranty1 yr.
Compliance and Restrictions
This product contains a chemical that is regulated under California Proposition 65.
Warning: This product contains a chemical known to the State of California to cause cancer.
Warning: This product contains a chemical known to the State of California to cause birth defects or other reproductive harm.
Displaying repair parts for model: M265
Alternate Search Terms
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.
Ask your questions. Share your answers.
Yes that will work providing you are not lifting the fluid beyond 10' straight up..
I hope this answers your question, thanks for using Grainger Ask & Answer!
Grainger is neither responsible for, not does it endorse, the content of any statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger.