Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
Blower, Draft Inducer
- Item # 4C731
- Mfr. Model # D-3
- NSN # 4140-01-334-3783
- UNSPSC # 40101601
- Catalog Page # 4319
- Shipping Weight 10.0 lbs.
- ItemDraft Inducer
- Vent Pipe Dia. (In.)5 to 8
- Height (In.)9-1/8
- Width (In.)9-1/2
- Depth (In.)7
- Cut Out Required3-1/8 x 8-5/8
- ApplicationProvides Positive Draft for Smokepipe and Aids Proper Exhaust of Combustion Gas.
- Construction MaterialAluminized Steel Housing and Blower Wheel
- RemarksView Catalog Page For Selection Criteria
Compliance and Restrictions
Alternate Search Terms
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.
Ask your questions. Share your answers.
This blower is designed for draft induction for gas fired heaters. The CFM’s will change based on vent pipe size and flue gas temperature.
5” pipe @ 270° flue gas 190CFM, @ 390° flue gas 166CFM, @ 530° flue gas 163CFM.
6” pipe @ 270° flue gas 246CFM, @ 390° flue gas 190CFM, @ 530° flue gas 169CFM.
7” pipe @ 270° flue gas 259CFM, @ 390° flue gas 166CFM, @ 530° flue gas 118CFM.
8” pipe @ 270° flue gas 217CFM, @ 390° flue gas 110CFM, @ 530° flue gas 65CFM.
Thank you for using Grainger Ask and Answer.
Grainger is neither responsible for, not does it endorse, the content of any statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger.