Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
Hot Water Circulator Pump, SS, 1/40 HP
- Item # 3GZW3
- Mfr. Model # 006-ST4-1
- UNSPSC # 40151504
- Catalog Page # 3768
- Shipping Weight 4.95 lbs.
- ItemHot Water Circulator Pump
- Pump TypeIn Line, Wet Rotor
- Inlet/Outlet Size3/4"
- Connection StyleNPT
- Face to Face Dimension4"
- Max. GPM @ Head11 gpm @ 1 ft.
- Best Efficiency GPM @ Head6 gpm @ 6 ft.
- Min. GPM @ Head2 gpm @ 9 ft.
- Shut-Off9.5 ft.
- Housing MaterialStainless Steel
- Drive TypeDirect
- Loop ConfigurationOpen
- Flange/Union IncludedNo
- Max. Operating Pressure125 psi
- Max. Temp.220 Degrees F
- Number of Speeds1
- Thermal ProtectionImpedance
- Pump MountIn Line
- Impeller MaterialNoryl(R)
- Shaft MaterialCeramic
- Mechanical SealNo
- Featureswet rotor, maintenance free
- Manufacturers Warranty Length3 yr.
- ComplianceLow Lead,NSF-372
Compliance and Restrictions
This product has been certified by a third party to be compliant with the “Safe Drinking Water Act” requirements for low lead in potable (human consumption - drinking and cooking) and non-potable water applications (non-human consumption).
Alternate Search Terms
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.
Ask your questions. Share your answers.
This pump needs to be mounted horizontally only, it will not work vertically and will void the warranty..
Thanks for using Grainger Ask & Answer
Grainger is neither responsible for, not does it endorse, the content of any statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger.