Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
Electric Tankless Water Heater, Undersink, Point-of-Use, 9000/12,000 Watts, 50 Amps AC
- Item # 49X684
- Mfr. Model # DHC-E 12
- UNSPSC # 40101825
- Catalog Page # N/A
- Shipping Weight 7.8 lbs.
- Item Electric Tankless Water Heater
- Water Heater Design Point-of-Use
- Water Heater Application Undersink
- Watts 9000/12,000
- Amps AC 50
- Voltage 208/240VAC
- Phase 1
- Min. Flow Activation 0.37 gpm
- Temp. Range 86 Degrees to 140 Degrees F
- Water Connection 3/4" NPT
- Temp. Rise @ 1.5 GPM 41/55 Degrees F
- Temp. Rise @ 6.0 GPM 10/14 Degrees F
- Temp. Rise @ 2.5 GPM 25/33 Degrees F
- Temp. Rise @ 4.0 GPM 15/20 Degrees F
- Temp. Rise @ 8.0 GPM 8/10 Degrees F
- Residential / Commercial Commercial
- Elements Copper Sheathed Housed in Cylinder
- Mounting Vertical
- Pressure Range 150 psi
- Wire Size 6 AWG
- Height 14-3/16"
- Width 7-7/8"
- Depth 4-1/8"
- Features Advanced Microprocessor Control, Code Compliance Made Easy, No Scalding, Simple Plumbing System Design, Sleek Design Fits In Anywhere, Seismic Proof Construction, Superior, German Engineered for Proven Reliability
- Standards ANSI/UL Stdandard 499, Certi ed To CAN/CSA E335-1 & E335-2-35
Compliance and Restrictions
This product has been certified by a third party to be compliant with the “Safe Drinking Water Act” requirements for low lead in potable (human consumption - drinking and cooking) and non-potable water applications (non-human consumption).
Alternate Search Terms
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.