Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
Soft Start, 208-690VAC, 210A, Altistart48
- Item # 6VMA5
- Mfr. Model # ATS48C21Y
- UNSPSC # 39121521
- Catalog Page # 336
- Shipping Weight 49.68 lbs.
- ItemSoft Start
- TypeHMI Control
- HP @ 3 Phase - 208V60
- HP @ 3 Phase - 230V75
- HP @ 3 Phase - 460V150
- HP @ 3 Phase - 575V200
- Output Current210A
- Input Voltage208-690VAC
- Output Voltage208-690VAC
- Control Voltage110-230VAC
- Ramp Time1 - 60 Seconds
- Start TypeExclusive Torque Control System (TSC) for Linear Starting and Stopping, or By Current Limit Adjustment up to 5 Times the Device Rating
- Stop Time1 to 60 seconds (Adjustable)
- Enclosure RatingIP20
- Inputs/Outputs4 Logic Inputs, 1 PTC Probe Analog Input, 1 Analog Output, 3 Relay Outputs
- ApplicationConstant & Variable Torque
- IncludesExclusive motor Torque Control System (TCS)
- Starting TorqueMax 400%
- Communication PortModbus
- Display3 Seven -Segment display
- StandardsUL File No. E184727, CSA File 164581, IEC/EN 60947-4-2, EMC classes A and B, CE,UL ,CSA,DNV,C-Tick,GOST, CCC,NOM,SERPRO AND TCF
Compliance and Restrictions
Alternate Search Terms
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.
Grainger is neither responsible for, not does it endorse, the content of any statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger.