Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
Gas Valve, Standard Opening, 70,000 BtuH
- Item # 6KXC7
- Mfr. Model # 710-502
- UNSPSC # 40141604
- Catalog Page # 4227
- Shipping Weight 1.7 lbs.
- Item Gas Valve
- BtuH Capacity 70,000
- Valve Type Standard Opening
- Coil Volts 750mV
- Gas Type NG/LP
- Inlet Size 1/2"
- Outlet Size 1/2"
- LP Conversion Kit 26X372
- Side Taps Yes
- Inlet Pressure Tap Yes
- Reducer Bushing Kit (2) 1/2 X 3/8"
- Ambient Temp. Range -40 to 175 Degrees F
- Amps AC .2
- Pressure Setting Range 3.5" WC
- For Use With RV's And Other Applications With Limited Space
- Includes (2) 1/2 X 3/8" Reducer Bushings
Compliance and Restrictions
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.
Ask your questions. Share your answers.
The 710-502 looks identical to the valve I currently have installed. The terminals and wiring are identical. However, my valve has a thermocouple which screws into a fitting and the photos I see of the 710-502 have a wire from the terminal block to a plug type connector instead of a threaded fitting.
Is the thermocouple replaced on this valve with the thermopile only?
The type of thermopile the new valve accepts is different now. You will want to look at part number 2E446. This is a 750 milivolt thermocouple with spade terminals.
Thank you for using Grainger Ask and Answer.
Grainger is neither responsible for, not does it endorse, the content of any statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger.