Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
- ItemCondensate Pump
- Pump TypeCompact Submersible
- Max. Pressure4.3 psi
- Reservoir CapacityNo Reservoir
- Discharge1/4" MNPT
- Float MaterialABS Plastic
- Shut-Off10 ft.
- Max. Temp.120 Degrees F
- Cord Length6 ft.
- Shaft MaterialStainless Steel
- Includes6 ft. Power Cord, Thermal Overload Protector, Polyethylene Screen, 1/4" Discharge Elbow
- GPH of Water @ 1 Ft. of Head205
- GPH of Water @ 5 Ft. of Head145
- GPH of Water @ 9 Ft. of Head25
Compliance and Restrictions
This product contains a chemical that is regulated under California Proposition 65.
Warning: This product contains a chemical known to the State of California to cause cancer.
Warning: This product contains a chemical known to the State of California to cause birth defects or other reproductive harm.
Alternate Search Terms
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.
Ask your questions. Share your answers.
Finding the answer to my first question was not simple, straightforward, or intuitive.
Well to answer this it would require some more info, but for the most part. This pump will lift the fluid 10ft max, at the apex of the ideally less than 10ft you put a drop loop in the tubing so that water will siphon away from the pump. This will prevent the fluid from "spilling back" other wise you can use a Check Valve in the outlet of the pump.
I hope this answers your question, thanks for using Grainger Ask & Answer!
This pump is designed to opperate with a 2.5" on and 1" to 1.5" off. The Float switch could be moved but would void the warranty, perhaps another unit would be more suitable. And no there is no tank included, A 3P732 is a uit that has a reservoir included.
I hope this anwsers your question, thanks for using Grainger Ask & Answer
Grainger is neither responsible for, not does it endorse, the content of any statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger.