Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
Smoke Alarm, Ionization, 120VAC, 9V
- Item # 1XTG6
- Mfr. Model # i12040
- UNSPSC # 46191501
- Catalog Page # 2487
- Shipping Weight 0.8 lbs.
- ItemSmoke Alarm
- Detection MethodIonization
- Interconnection CapabilityUp to 24 Units
- Power Source120VAC, 9V
- Audible Alert85dB @ 10 ft., Horn
- Visual AlertRed LED
- Digital ReadoutNo
- Battery BackupYes
- FeaturesAlarm Memory
- Hush ButtonYes
- Test ButtonYes
- Locking PinYes
- Operating Temp.40 Degrees to 100 Degrees F
- Manufacturers Warranty Length5 Year Limited
Compliance and Restrictions
Hazardous material - General
Alternate Search Terms
Product Reviews Disclaimer:
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.
Ask your questions. Share your answers.
To replace or install the batteries, you must first remove the alarm from the trim ring by following the ALARM REMOVAL instructions at the beginning of this section. After alarm has been removed, you can open the battery door and install or replace the battery. Battery installation instructions are provided on the inside of the battery door. When installing the battery, press the battery reminder finger down into the battery compartment and install the battery.This smoke alarm uses a 9V carbon backup battery (alkaline and lithium batteries may also be used). A fresh battery should last for one year under normal operating conditions. This alarm has a low/missing battery monitor circuit which will cause the alarm to “chirp” approximately every 30-40 seconds for a minimum of seven (7) days when the battery gets low. Replace the battery when this condition occurs. If the alarm is located outside the bedroom or on a different floor, it may not wake up a sound sleeper. The use of alcohol or drugs may also impair one’s ability to hear the smoke alarm. For maximum protection,
a smoke alarm should be installed in each sleeping area on every level of a home. Although smoke alarms can help save lives by providing an early warning of a fire, they are not a substitute for an insurance policy. Home owners and renters should have adequate insurance to protect their lives and property. Install and maintain Fire extinguishers on every level of the home and in the kitchen, basement and garage. Know how to use a fire extinguisher prior to an emergency.
The model #i12040 ionization smoke alarm were installed in august 2010. New 9V batteries were put in every year. There was no smoke or humidity in the house at the time. Very dis-tressing when one is fast asleep.
If any amount of dust or insects get into the monitor, which happens quite often, it can set the sensor in the monitor off. It is suggested to vacuum and clean the detector once a month around the outer edge to collect any dust or insects.
Thank you for using Grainger Ask and Answer
Ask and Answer Disclaimer:
Grainger is neither responsible for, not does it endorse, the content of any statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger.
The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any statements posted, including statements posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such statements.
Use of any linked web site provided in a post is at the user's own risk. This site should not replace the use by you of any technical product manual or other professional resource or adviser available to you.
The source for the answers given by Grainger in Ask and Answer are based on the information provided with the question, which may not be complete or may not apply to other situations, and based on product literature and informational materials, the content of which is provided by Grainger's product suppliers. Grainger disclaims liability for any information it provides in Ask and Answer which later may be alleged or determined by a court of law to be inaccurate or incorrect.
The answers given by Grainger in Ask and Answer are not intended to replace or supplement any professional, engineering or other consultation services available to its product users. Always read, understand, and follow the product information and instructions provided by the manufacturer. same on category AAA as well