Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
Ventilator Dehumidification Control
- Item # 2E574
- Mfr. Model # H46C1166
- NSN # 5930-00-102-0894
- UNSPSC # 40101903
- Catalog Page # 4223
- Shipping Weight 0.9 lbs.
- Item Dehumidifier Controller
- Mounting Wall
- Adjustable Range 20 to 80% RH
- Differential (RH %) 4 to 6
- Voltage 115
- Contact Rating (Amps) 7.5
- Switch Action Closes on Humidity Rise, Opens on Fall
- Switch Type SPST
- Height (In.) 4-3/4
- Width (In.) 3
- Depth (In.) 2-1/8
- Agency Compliance UL
- Includes White Plastic Cover and Metal Adapter Plate for Vertical Switch Box Mounting, Wiring Diagram
Compliance and Restrictions
Alternate Search Terms
Product Reviews Disclaimer:
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.
Ask your questions. Share your answers.
The H46 makes contact on a relative humidity rise to the setpoint to start the dehumidifier. On a decrease in relative humidity to the setpoint (minus the differential), the switch breaks contact to stop the dehumidifier. Turn the knob clockwise to the setting stop to place the H46 in the On position. Turn the knob counterclockwise to the setting stop to place the H46 in the Off position.
If you need additional documents please contact us at 1-800-Grainger. Thank you for using Grainger.com Ask & Answer.
Grainger is neither responsible for, not does it endorse, the content of any statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger.