Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
Pilot Burner, B Bracket
- Item # 1D289
- Mfr. Model # Q314A4586
- UNSPSC # 40101833
- Catalog Page # 4226
- Shipping Weight 0.2 lbs.
- Item Pilot Assembly
- Type Non Primary-Aerated
- Gas Type LP/NG
- Orifice Dia. (In.) NG 0.018, LP .010
- Tip Style F, Flame Pattern Front
- Special Information Pilot Burner For Natural or LP gas With A BCR-18 Orifice, Front Single Tip Style, With 1/4" Gas Connection, B Type Bracket
- Includes NG & LP orifice
- Package Quantity 1
Compliance and Restrictions
Alternate Search Terms
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.
Ask your questions. Share your answers.
From the description of your symptoms, it does sound like one of two possible issues:
1.) Either the incorrect orifice is installed, or,
2.) Pilot Pressure may be too high.
We hope this information is of use to you.
Honeywell Customer Care
The pilot flame should not be that large. This pilot comes with an orifice for natural gas and propane. You need to be sure you have the correct orifice for the gas you are using.
Thank you for using Grainger Ask and Answer.
Grainger is neither responsible for, not does it endorse, the content of any statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger.