Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
- ItemAutomatic Standby Generator
- Engine Cooling MethodLiquid
- kW45 LP/45 NG
- kVA Rating56.25
- Enclosure MaterialSteel
- Fuel TypeNatural Gas/Propane
- Engine BrandGenerac
- Engine Size2.4L
- Engine RPM3600
- NG Consumption @ Half Load604 cu. ft./hr.
- LP Consumption @ Half Load6.8 gph
- Sound Level dBA61 Exercising At 7m or 65 Normal Operation At 7m
- Automatic Volts RegulationYes
- Battery IncludedNo
- 12VDC Battery ChargerYes
- Battery Requirements24F
- Engine (Block Heater)No
- Fault Indicator Lights7
- Fuel NPT Pipe Connection Sz.3/4"
- High Temp. AlarmYes
- Low Coolant Level AlarmYes
- Low Oil Pressure AlarmYes
- Min. Gas Pressure @ Generator (In WC)5 to 7
- Over Crank ProtectionYes
- Power Factor0.8
- Repeat of Exercise Cycle7
- Run Time Hour MeterYes
- Over SpeedYes
- IncludesOil Drain Extension, Radiator Drain Extension, Battery Cables and Rack, Flex Fuel Line, Fan and Belt Guards, Instruction Sheets
- StandardsNEC, UL 2200
Compliance and Restrictions
This product contains a chemical that is regulated under California Proposition 65.
Warning: This product contains a chemical known to the State of California to cause cancer.
Warning: This product contains a chemical known to the State of California to cause birth defects or other reproductive harm.
Alternate Search Terms
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.
Grainger is neither responsible for, not does it endorse, the content of any statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger.