Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
Electric Infrared Heater, Indoor/Outdoor, Ceiling/Suspended, Voltage 480, Watts 7300
- Item # 3UD67
- Mfr. Model # 462-60-THSS-480V
- UNSPSC # 40101824
- Catalog Page # 3838
- Shipping Weight 29.1 lbs.
- Item Electric Infrared Heater
- Indoor/Outdoor Indoor/Outdoor
- Element Type Quartz Lamp, Clear
- Radiant Efficiency 96%
- Mounting Type Ceiling/Suspended
- Watts 7300
- BtuH Output 24,908
- Voltage 480
- Amps @ 1 Phase 15.20
- Amps @ 3 Phase 8.80
- Beam Pattern 60 Degrees
- Number of Lamps 2
- Infrared Electromagnetic Wave Type Short Wave
- Height 11"
- Width 15"
- Length 46"
- Housing Material 20 ga. Stainless Steel
- Phase 1
- Finish Stainless Steel
- Cord Type Hard Wired
- Standards ETL
- Includes (6) High Temperature Leads
- Heat Pattern Coverage @ Floor (10 Ft.) 15 x 12
- Heat Pattern Coverage @ Floor (12 Ft.) 17 x 14
- Heat Pattern Coverage @ Floor (14 Ft.) 19 x 16
- Heat Pattern Coverage @ Floor (16 Ft.) 22 x 18
- Heat Pattern Coverage @ Floor (18 Ft.) 24 x 21
- Heat Pattern Coverage @ Floor (8 Ft.) 12 x 12
- Watts Delivered/Sq.-Ft. 10 40.6
- Watts Delivered/Sq.-Ft. 12 30.7
- Watts Delivered/Sq.-Ft. 14 24.0
- Watts Delivered/Sq.-Ft. 16 18.9
- Watts Delivered/Sq.-Ft. 18 14.5
- Watts Delivered/Sq.-Ft. 8 52.9
Compliance and Restrictions
Need help finding replacement parts? Please use the list below or call 1-800-GRAINGER (472-4643)
Alternate Search Terms
Product Reviews Disclaimer:
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.
Ask your questions. Share your answers.
Fostoria # 630-36489
Grainger # 1UMN5
Grainger is neither responsible for, not does it endorse, the content of any statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger.