Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
This item has been discontinued and is unavailable for purchase. Check the Alternate Products selection below for options. For more information call 1-800-GRAINGER (472-4643).
Blower, DD, 115V, 4 Speed
- Item # 19F693
- Mfr. Model # 70265431
- UNSPSC # 40101601
- Catalog Page # 4161
- Shipping Weight 44.0 lbs.
- TypeDouble Inlet Forward Curve, Direct Drive, With Motor
- Wheel Dia. (In.)10-5/8
- Wheel Width (In.)10-5/8
- CFM Range2400 to 230 @ 0.000-In SP to 1.700-In SP
- CFM @ 0.000-In. SP2400, 1800, 1450, 1220
- CFM @ 0.300-In. SP2380, 1760, 1420, 1185
- CFM @ 0.400-In. SP2350, 1750, 1410, 1180
- CFM @ 0.500-In. SP2335, 1720, 1395, 1170
- CFM @ 0.600-In. SP2300, 1675, 1365, 1150
- CFM @ 0.700-In. SP2210, 1650, 1300, 1080
- CFM @ 0.800-In. SP2130, 1550, 1220, 1010
- CFM @ 0.900-In. SP1900, 1390, 1125, 925
- CFM @ 1.000-In. SP1720, 1225, 1010, 790
- CFM @ 1.10-In. SP1440, 1030, 845, 620
- CFM @ 1.200-In. SP1160, 840, 650, 465
- CFM @ 1.250-In. SP955, 735, 570, 380
- CFM @ 1.30-In. SP750, 635, 490, 300
- CFM @ 1.40-In. SP540, 435, 340, 245
- CFM @ 1.500-In. SP430, 325, 240, 120
- CFM @ 1.600-In. SP320, 215, 150, -
- CFM @ 1.70-In. SP230, 100, -, -
- CFM @ 1.80-In. SP-, -, -, -
- Max. Inlet Temp. (Deg. F)104
- Max. Ambient Temp. (F)104
- Full Load Amps5.6
- Motor HP1/2
- Motor RPM1125
- Motor TypePSC
- Bearing TypePermanently Lubricated Sleeve Bearing
- Motor EnclosureVented
- Blower RPM1100
- Housing Height (In.)15-1/16
- Housing Width (In.)13-3/16
- Housing Depth (In.)19-3/8
- Discharge Height (In.)9-1/8
- Discharge Width (In.)13-1/8
- Housing MaterialAluminized Steel
- Housing FinishAluminum
- Wheel MaterialGalvanized Steel
- Agency ComplianceUL/CSA Motor Recognized
Compliance and Restrictions
Alternate Search Terms
Product Reviews Disclaimer:
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.
Grainger is neither responsible for, not does it endorse, the content of any statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger.