Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
Surge Protection Device, 1 Phase, 240V
- Item # 18K856
- Mfr. Model # TDX100C240
- UNSPSC # 39121610
- Catalog Page # 294
- Shipping Weight 2.45 lbs.
- Item Surge Protection Device
- Phase 1
- Voltage 240VAC
- Max. Continuing Operating Voltage 275VAC
- Voltage Protection Rating 1000V (L-G, L-N, N-G)
- Nominal Discharge Current 40kA
- Modes of Protection L-G, L-N, N-G
- Filtering / Nonfiltering Nonfiltering
- Modular / Nonmodular Modular
- Mounting Style Panelboard, 3/4" Straight Nipple (Optional Flush Mounting Plate for Drywall)
- Enclosure Material Aluminum
- Enclosure NEMA Rating 4
- IP Rating 65
- Length 6.02"
- Width 3.31"
- Depth 3.07"
- Lightning Impulse Current 12kA
- Max. Surge Current Per Phase 100kA
- Short Circuit Current Rating 200kA
- Number of Wires 2 Wires + Ground
- Standards CE, IEC 61643-1, ETL Listed to UL 1449 Edition 3 Type 1/2
- Green Certification or Other Recognition RoHS Compliant
Compliance and Restrictions
Green Product - This item has been designated by the manufacturer as an environmentally preferable product (EPP) because this item is RoHS Compliant.
Alternate Search Terms
- Surge Protectors (919)
- Electrical Surge Protectors (915)
- TVSS (Transient Voltage Surge Suppressors) (490)
- TVSS (Transient Voltage) Surge Protectors/Suppressors (488)
- Surge Arrestors (485)
- Electrical Surge (423)
- Hard-Wired Surge Protectors/Suppressors (423)
- Power Surge Protectors (423)
- SPD (Surge Protection Devices) (423)
- Surge Protection (423)
Product Reviews Disclaimer:
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.
Grainger is neither responsible for, not does it endorse, the content of any statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger.