Using 360° Viewing:
- Rotate: Use top-to-bottom, side-to-side by use of mouse arrow.
- Zoom In: Double click on image.
- Zoom Out/Reset: Put photo at full zoom & then double click.
Encapsulated Timer Relay, 300sec, 5Pin, 1NO
- Item # 6A859
- Mfr. Model # 6A859
- UNSPSC # 39121519
- Catalog Page # 353
- Shipping Weight 0.2 lbs.
- ItemEncapsulated Timer Relay
- OutputSolid State
- FunctionOff Delay
- Contact Form1NO
- Contact Amp Rating (Resistive)1A
- Input Voltage24 to 240VAC
- Min. Time Setting15 sec.
- Max. Time Setting300 sec.
- Adjustment MethodPotentiometer
Compliance and Restrictions
Alternate Search Terms
Grainger is neither responsible for, nor does it endorse, the content of any product review or statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger. The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any product review or statements posted, including those posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such product review or statements. Use of any linked web site provided in a product review or post is at the user's own risk.
Ask your questions. Share your answers.
2nd do you also make this exact relay for 12 V DC? Thanks
Thank you for using Grainger Ask & Answer
Power is applied to the coil at all times ( terminals 2 & 3). Upon CLOSURE of the start switch (a "dry" external contact [no voltage], terminals 6 & 7), the contacts transfer, either connecting normally open contact [terminal 1] to allow voltage to go to the load the load. When the start switch [terminals 6 and 7] is OPENED, the OFF DELAY timing
period begins. The contacts stay in the transferred position until the OFF DELAY timing period ends. They then return to their original position (the load then turns off) and the unit is ready for a new cycle.
Do not put voltage to terminals 6 & 7, or else you will fry this Solid State relay.
The load amperage cannot exceed the Amp rating of 1A, or else this relay will be damaged.
Thank you for using Grainger Ask and Answer.
Grainger is neither responsible for, not does it endorse, the content of any statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger.