Filter Results By
A kink in a cable or an exposed electrical wire might mean disaster for a business that relies on technology and electricity to keep running. With durable wireways from Grainger, this never has to be a concern. Wireways and wire ducts keep electrical equipment running by protecting the cords and wires that are essential for them to work well. Whether a company is adding a new wing and needs to protect the wiring or is adding new technology and needs to add wiring to an existing setup, these wireways are the tools necessary to do the job well.
- CABLOFILItem # 1ATP4
- COPEItem # 2HCP1
- COPEItem # 2HCN6
- COPEItem # 2HCN9
- COPEItem # 2HCL5
- CABLOFILItem # 4GVX4
- WIEGMANNItem # 2VE55
- CABLOFILItem # 4GVX6
- CABLOFILItem # 4GVX1
- WIEGMANNItem # 2VE20
- CABLOFILItem # 1ATN2
- CABLOFILItem # 1ATN4
- HOFFMANItem # 32FL84
- CABLOFILItem # 4JWT1
- COPEItem # 2HCN3
Ask your questions. Share your answers.
Here are the definitions of each item from the National Fire Protection Agency(NFPA) 70, National Electric Code (NEC) 2008:
NEC 376.2 Metal Wireways. Sheet metal troughs with hinged or removable covers for housing and protecting electrical wires and cable and in which conductors are laid in place after the wireway has been installed as a complete system.
NEC 392.2 Cable Tray System. A unit or assembly of units or sections and associated fittings forming a structural system used to securely fasten or support cables and raceways.
NEC 392.3 Uses Permitted. Cable tray shall be permitted to be used as a support system for service conductors, feeders, branch circuits, communications circuits, control circuits, and signaling circuits.
Thank you for using Grainger Ask & Answer.
Ask and Answer Disclaimer:
Grainger is neither responsible for, not does it endorse, the content of any statement posted. Any statements posted constitute the statements of the poster and are not the statements of Grainger.
The statements posted by Grainger employees with the Grainger employee badge represent the views of such employees and are not the statements of Grainger. Grainger makes no representations as to the appropriateness, accuracy, completeness, correctness, currentness, suitability, or validity of any statements posted, including statements posted by employees with the Grainger employee badge, and is not liable for any losses, injuries or damages which may result from any such statements.
Use of any linked web site provided in a post is at the user's own risk. This site should not replace the use by you of any technical product manual or other professional resource or adviser available to you.
The source for the answers given by Grainger in Ask and Answer are based on the information provided with the question, which may not be complete or may not apply to other situations, and based on product literature and informational materials, the content of which is provided by Grainger's product suppliers. Grainger disclaims liability for any information it provides in Ask and Answer which later may be alleged or determined by a court of law to be inaccurate or incorrect.
The answers given by Grainger in Ask and Answer are not intended to replace or supplement any professional, engineering or other consultation services available to its product users. Always read, understand, and follow the product information and instructions provided by the manufacturer. same on category AAA as well